Protect Your Plant With Ultrasonic Gas Detection
Add a Critical Layer of Protection to Your Fixed Gas Detection System
Flammable gas leaks are a real threat to workers and assets across the process industry. If they are not detected swiftly, they can quickly escalate into devastating fires and explosions. Ultrasonic gas detection helps you locate gas leaks at the speed of sound to mitigate catastrophic consequences and minimize disruption to plant operation. Ultrasonic gas detectors can ‘hear’ the ultrasounds emitted by a gas leak, right from the start and under harsh weather conditions. This way, you can deal with a gas event early to protect your plant and avoid costly disruption.With ultrasonic detectors in place, you will gain a vital layer of protection against flammable gases. A layered system that integrates a variety of gas and flame detection technologies ensures optimal protection against flammable gas risks.
SEARCH. DETECT. PROTECT.
A robust and reliable gas-leak detection device, Searchzone Sonik™ will efficiently “hear” the loss of containment of any high-pressure gas within its listening zone. As it responds to the ultrasonic sound pressure level produced by pressurized gas leaks, it is therefore unaffected by environmental conditions. Searchzone Sonik™ is factory calibrated. Its robust sealed design with no moving parts and the advanced solid-state sensor allow for mounting in any orientation, even in the harshest environments. The acoustic gas leak detector will respond quickly to a gas leak within a sensing range radius of typically 20m (65 ft), dependent upon background noise.
Learn How You Can Leverage Ultrasonic Detection Within A Layered Safety Strategy
Detecting a gas leak early is key to preventing major disruption to plant operations. This is where ultrasonic gas detection technology is superior. This technology can ‘hear’ the ultrasounds emitted by escaping gas at the speed of sound. Even a small and low-pressure leak within a 20 m range* can be identified, buying you critical time to respond.
However, ultrasonic detection alone isn’t enough. Only pressurized gas can cause an ultrasonic detector to activate, meaning non-pressurized leaks will never be heard. Interference from other ultrasonic noise sources present in the application can be louder than a small leak. Finally, ultrasonic gas leak detection will alert you to a leak but won’t provide any indication of the gas type or concentration.
Open path infrared (IR) detection offers an extra layer of protection against flammable gases that may not have been heard by the ultrasonic layer. It can detect flammable hydrocarbons up to a 330 meter range, even at low concentrations, greatly increasing the chances of finding a leak. Unlike ultrasonic detection, it also provides critical data on threat levels based on gas concentration/size, enabling you to make informed decisions.
But even open path IR detection isn’t a one-size-fits-all solution. Since the gas must physically pass between the transmitter/receiver pair to activate an alarm, gas leaks may go undetected under windy conditions. Open path IR is also unsuitable for confined spaces.
Point IR detection is often the basic option when it comes to flammable gas monitoring. Unlike open path IR, it can be deployed in small areas and confined spaces, especially near potential leak sources such as valves, flanges, and pumps, offering a basic layer of protection. A key advantage of deploying point detectors is that they measure actual gas concentrations at a point in space and time. By installing multiple devices, you can gain an accurate map of a gas release event.
Similar to ultrasonic and open path IR detection, point IR detection has its limitations, which is why it should be a part of a layered approach. Its main downsides are its limited range and the fact that the gas may never reach the sensor in windy conditions like open path IR.
Flame detection is the final, critical layer of protection when working around flammable gases. It quickly detects the radiant energy produced by a fire’s flames, giving you time to intervene before things escalate into a disaster. There are different technologies to choose from, but multi-spectrum triple IR flame detection is generally recommended for process industry applications. It can detect hydrocarbon and non-hydrocarbon fuel fires under most environmental conditions. Even a small 0.09 m2 Heptane reference fire can be detected from a distance of over 60 m. Ultimately, the use of multiple layers of detection significantly increases your chances of detecting flammable gas leaks before they escalate into catastrophic fires and explosions.